||CABLE / CONDUIT
||3 METRE** 2.5mm2
||5 METRE* 2.5mm2
|PE N1 L1 L2 L3
4m tap-offs and other alternatives are available on request via MK Design Service
Tap-offs are supplied as single cables inside steel flexible conduit, except those with ‘C’ suffix, which are supplied with 3 or 4 core LSF flex, as appropriate.
* Unfused tap-offs in excess of 3m can only be used on powertrack protected with a 32A (or less) circuit protection device.
** When fully stretched to ensure the conductor lengths do not exceed 3m to comply with BS 7671:2008 17th Edition IEE Wiring Regulations to ensure the conduit remains
flexible this is then shortened by a further 0.1 - 0.2 of slack when wired to a module.
Add ‘DE’ suffix for Dual Earth High Integrity Earthing††, e.g. UT51301DE.
Unfused tap-offs - High Integrity Earthing†† as standard.
Add ‘607’ suffix for High Integrity Earthing††, e.g. UT51301607.
† Key codes shown are from the perspective of the Power Track socket with the keycode in the top right corner.
The tap-off key code will be a mirror image when viewed from underneath.